SCB10-800KVA Dry type transformer It is safe, flame retardant, fireproof and pollution-free and can be directly installed in the load center. Maintenance free and easy to install. It has good moisture proof function and can be put into operation without pre drying after shutdown. Low loss, low partial discharge, low noise and forced 120%
rated load operation under forced air cooling condition. Equipped with a perfect temperature protection and control system to provide reliable guarantee for the safe operation of transformer, the reliability index of the product has reached the advanced level in China. SCB10-800KVA Dry type transformer It is a new type of energy saving. Dry type transformer The transformer is low noise, environmental protection, safety, service, high quality transformer material, and scientific formula. The advanced detection equipment is produced by strict process. The product has the characteristics of high reliability and long service life.
Common parameters of SCB10-800KVA dry type transformer
 length * width * height: 1480*1170*1546.5
 installation gauge: 820*1070
 stainless steel shell size is long * width * high 1800*1550*1850
 self weight: 3600Kg
 no load loss (P0):2450W
 load loss (Pk) 11730W
 no load current (Io) 1%
 short circuit impedance (Uk) 6%
SCB10-800KVA dry type transformer introduction:
S: indicates that the transformer is a three-phase transformer.
C: indicates that the transformer is constructed by epoxy resin.
B: represents the winding of the winding used in the transformer winding.
10: the transformer is 10 type.
800: the rated capacity of the transformer is 800KVA.
Standards for product implementation:
1, GB1094.11-2007 "power transformer second parts: dry type transformer".
2, GB/T 10228-2008 "dry power transformer technical parameters and requirements" and entrusted requirements.
3, GB1094.1-1996 general principles of first parts of power transformers.
4, GB1094.3-2003 "third parts of the power transformer insulation level, insulation test, and external insulation air gap".
5, GB1094.5-2008 "fifth parts of power transformer withstand short circuit capability".
6, GB/T1094.10-2003 "power transformer tenth parts sound level determination"